Welcome to Elgas Training The following training videos are not a substitute for an actual training session. Video: Safe Decanting of LPGas for BBQ Cylinders LPG Decanting Assessment (PDF download) LPG Decant Certificate (PDF download) Video: Safe Decanting of LP Gas for Forklift Cylinders LPG Forklift Cylinder Refilling Assessment (PDF download) LPG Forklift Cylinder Refilling Certificate (PDF download) Video: Safe Filling of Forklift Cylinders by Pump Fill Video: The Safe Changeover of Forklift Cylinders These videos are only a supplement and refresher for those who have completed the applicable Elgas training course. It is not the complete training course and other training materials apply. LPG decanting must not be attempted by untrained individuals. Safety measures that should be considered when decanting LPG: ♦ Operators engaged in LPG decanting must be able to demonstrate competency in decanting procedures and emergencies, and in using personal protective equipment (PPE) appropriate for the task. Untrained individuals should not be allowed to perform decanting. ♦ Cylinders must be inspected and have a current inspection mark. ♦ Do not refill cylinders that are damaged or corroded. ♦ Decanting area must be a safe distance from fuel dispensers, flammable materials, tanks containing dangerous goods, public places, and building entries and exits. ♦ Protect LPG cylinders, attachments and associated pipe work from damage. This includes protecting the main decanting cylinder from a vehicle collision. ♦ Eliminate all ignition sources. Devices such as ice freezers, static electricity and smoking are not to be introduced into a hazardous area. ♦ Operators must understand the nature of static electricity, and the associated precautions included in the safety procedures. ♦ Ensure operators are trained to identify any worn or damaged parts in the decanting equipment. ♦ Display a notice reading ‘Flammable Gas, No Smoking’ (with letters at least 50mm high) as close as possible to the decanting area. ♦ Display a notice that outlines the procedure for decanting, including a warning to stop filling as soon as the maximum permitted level has been reached. As a minimum, the procedure should reflect all the safety requirements outlined in appendix J of AS/NZ1596. ♦ A trained operator must be present during the filling process. ♦ Do not any device to hold the dead man’s valve open. It must only be kept open by hand. ♦ Wear appropriate PPE during the decanting process. This includes gloves and safety glasses and cotton or anti-static clothes. ♦ Minimise the risk of static electricity by placing the cylinder to be filled on an electrically conductive and grounded stand. Do not use a plastic milk crate or any similar non-conducting type of stand. ♦ Before starting, touch the body of the decanting cylinder with bare hands to discharge any static electricity. ♦ Adequate fire protection must be provided. As a minimum, have a hose reel or powder-type extinguisher should be available in the decanting area. Agents & Distributors Agent Distributor Assessment This assessment tool is designed to check the candidate’s theoretical knowledge and understanding of the job task and record the responses given by a candidate against each of the questions posed. Agent & Distributor Manual Becoming an Elgas Agent or Distributor has many benefits, and with those benefits also come many responsibilities. This training manual covers the responsibilities you need to know about operating as an Agent / Distributor. You will receive additional support from your local Elgas branch staff and be visited by your local Elgas representative.